Factory Direct Re-Verber-Ray Replacement Parts
|Part #||Alt Part #||Description||Shipping Method|
Relay Panel with Two Relay Boards
|UPS or USPS|
|Notes||Used On||Voltage||Gas Type|
Relay panels or boards must be used anytime two or more two-stage heaters are operating on the same thermostat (or common vented). Relay panels are prewired and mounted inside one NEMA(1) enclosure. Available with 2 relays, 6 relays, or 10 relays per NEMA(1) box. Each relay can accommodate one heater. Each panel has one 40 V.A. transformer internally mounted. Relay boards can be (at the time of production) internally mounted into the burner box. This must be specified at the time of order. One board is needed per heater. An external transformer (eg. -4000-01V) will then be needed to power the control. HLRB are preferred over panels.
NOTE: HLRB’s are not necessary on DET3 Series.
|HL3, LD3||N / A||N / A|